508.1.2 Separation. The fire command center shall be separated from the remainder of the building by not less than a 2-hour fire barrier constructed in accordance with Section 707 of the International Building Code or horizontal assembly constructed in accordance with Section 711 of the International Building Code, or both.
[Statutory Authority: Chapter 19.27
RCW and RCW 19.27.031
. WSR 17-10-028, § 51-54A-0508, filed 4/25/17, effective 5/26/17. Statutory Authority: RCW 19.27A.031
and chapters 19.27
RCW. WSR 13-04-063, § 51-54A-0508, filed 2/1/13, effective 7/1/13.]